Does absorption minibar need suitable ventilation?
With both air inlet and air outlet ducts is the fundamental requirement upon a suitable design of ventilation. The location of air inlet must be lower than Minibar for cold air to enter air inlet, the total area should no less than 120cm2 and larger dimension would be better. The location of air outlet must higher than the appliance and should be as close as possible to the rear, the total area should no less than 120cm2 and larger dimension would be better. Please take the below picture for reference (the arrow shows the direction of air flow).
Need more professional suggest upon ventilation design, please contact us and your Wellway Service partner.